NO WATER PRODUCED. MOISTURE IS VENTED AWAY EVEN UPWARDS
Used For Restoration, Sea Vessels & Catering Industries.
74 Pint Desiccant Dehumidifier 110V / 60Hz
Equivalent to a 150 Pint Compressor Dehumidifier @65°F
Free Standing or Installed
Industrial dehumidifier EPD150 PRO stainless steel construction.Very small for its 74 pint capacity. Will dry 24/7 and dry even down to -20°C/-4°F. Can work up to 40°C/104°F.
Stainless Steel Inside & OutTough Enough Even for Hiring or Restoration
Can be carried by one person and transported easily with the carrying handles.Self regulating energy usage that adapts to air pressure differences using always the right amount of power to dry effectively
3 Hole Dehumidifier
Input process air is dust filtered & dried. Input air can be ducted in & out with a 125mm / 5″ duct. Wet air exhaust is 80mm / 3″ duct
Ecor Pro’s research shows that the EPD150 PRO will be four to seven times faster at drying buildings at low temperatures than a traditional compressor dehumidifiers
- Flexible Industrial Ducting 80mm / 3" Diameter Length 3m / 9' £ 50.00
- Flexible Industrial Ducting 80mm / 3" Diameter Length 6m / 18' £ 60.00
- Flexible Industrial Ducting 125mm / 5" Diameter Length 3m / 9' £ 55.00
- Flexible Industrial Ducting 125mm / 5" Diameter Length 6m / 18' £ 139.99
- FILTERDH Filter Three Pack for DH25XX, DH35XX, EPD150, EPD200 £ 20.00
- EPHUM110 Humidistat for DH2511, DH3511, EPD150, EPD200 £ 130.00
Highly Compact – Small 74 pint dehumidifier in the market.
Perfect for any climate.
Wet Air Exhaust – The EPD150 has one internal fan compared to two in the EPD200. Both do not produce water. The moisture is vented away allowing it to work in colder temperatures. The moisture is purged from the system by 15% of the process air. Dries with a small negative pressure.
This is a 3-Hole dehumidifier meaning that there is one fan inside. Part of the dried process air is turned around, heated and used to purge the internal adsorption wheel of moisture that can be then vented away.
15% of the air that is processed is expelled as wet air. This air needs to be replaced. Air from outside the room may be more humid. This is averted with a larger model.
Having the machine in the area being dried and recirculating the air is the most efficient way of drying. This system is "Negative Pressure. In a small enclosure, covered with plastic sheeting a frame is needed to ensure the tent maintains structure. Rooms generally are not air tight so in larger rooms air can leak under doors etc
3-hole systems have one advantage over 4-Hole systems. Around 60 Watts of energy will be retained in the process air flow with a 4-Hole system. Normally this is not a problem (Same energy as an old home light bulb) but if it is a variable air valve may be added to balance the system with regen air.
This assumes that the air from any variable inlet (variable in order to find balance of air flow) is colder than the air inside the room being dried. Typical applications will include buildings where heat generated by people is not covered fully by any air conditioning.