Positive or Negative Focus Flood Drying
NO WATER PRODUCED. MOISTURE IS VENTED AWAY. EVEN UPWARDS.
Ideal Flood Or Home Dryer. Restoration Safe.
74 Pint Desiccant Dehumidifier 110V / 60Hz.
Equivalent to a 150 Pint Compressor Dehumidifier @65°F.
Free Standing or Installed.
Industrial dehumidifier EPD150 steel construction with tough epoxy paint finish.Very small for its 74 pint capacity. Will dry 247 and dry even down to -20°C/-4°F. Can work up to 40°C/104°F.
Steel Inside & OutTough Enough Even for Hiring or Restoration
Can be carried by one person and transported easily with the carrying handles.Self regulating energy usage that adapts to air pressure differences using always the right amount of power to dry effectively
3 Hole Dehumidifier
Input process air is dust filtered & dried. Input air can be ducted in & out with a 125mm / 5″ duct. Wet air exhaust is 80mm / 3″ duct
Thus, Ecor Pro’s research shows that the EPD150 will be four to seven times faster at drying buildings at low temperatures than a traditional compressor dehumidifiers
- Flexible Industrial Ducting 80mm / 3" Diameter Length 3m / 9'
- Flexible Industrial Ducting 80mm / 3" Diameter Length 6m / 18'
- Flexible Industrial Ducting 125mm / 5" Diameter Length 3m / 9'
- Flexible Industrial Ducting 125mm / 5" Diameter Length 6m / 18'
- FILTERDH Filter Three Pack for DH25XX, DH35XX, EPD150, EPD200
- EPHUM110 Humidistat for DH2511, DH3511, EPD150, EPD200
Highly Compact – Small 74 pint dehumidifier in the market.
Duct Air-In & Out – The dehumidifier has all ducts fitted with flanges to allow ducting to be added with 125mm / 5″ hard or flexible ducting.
Perfect for any climate.
Wet Air Exhaust – Hence, EPD-150 has one internal fan compared to two in the EPD200. Both do not produce water. Furthermore, moisture is vented away, thus works in colder temperatures. Moisture is purged from the system by 15% of the process air – dries with slight negative pressure.
This is a 3-Hole dehumidifier meaning that there is one fan inside. Part of the dried process air is turned around, heated and used to purge the internal adsorption wheel of moisture that can be then vented away.
15% of the air that is processed is expelled as wet air. This air needs to be replaced. Air from outside the room may be more humid. This is averted with a larger model.
Having the machine in the area being dried and recirculating the air is the most efficient way of drying. This system is "Negative Pressure. In a small enclosure, covered with plastic sheeting a frame is needed to ensure the tent maintains structure. Rooms generally are not air tight so in larger rooms air can leak under doors etc
3-hole systems have one advantage over 4-Hole systems. Around 60 Watts of energy will be retained in the process air flow with a 4-Hole system. Normally this is not a problem (Same energy as an old home light bulb) but if it is a variable air valve may be added to balance the system with regen air.
This assumes that the air from any variable inlet (variable in order to find balance of air flow) is colder than the air inside the room being dried. Typical applications will include buildings where heat generated by people is not covered fully by any air conditioning.