Refrigerant Dehumidifier Overview
A Refrigerant or “Compressor” Dehumidifier Easy Guide
All Ecor Pro
Refrigerant Dehumidifiers Can Be Used In
TYPICAL INDUSTRIAL STORAGE
RULE OF THUMB
Industrial buildings will be higher ceilings, larger air flow from outside so need to consider a more powerful unit for the space than for a home for instance. Also great care must be given to what is being stores in the space. Farm produce for instance will contain a lot of water compared to sealed merchandise. High roofs take off 30%. For large moisture content conditions take 50%
POOL AREA & CHANGING ROOM
RULE OF THUMB
Pool areas obvious are more humid than hanging areas. If there is a large surface area of glass to keep clear in the pool area, consideration may be needed to create a curtain of dry air down the glass with the DSR12, 20 or LD800 dehumidifiers using additional duct work
Glass will act as a dehumidifier condensing moisture in the room and special consideration may be needed.
EU movie gives an outline of the features of the D850/D950 models
Integral humidistat and electronic controls
Wall bracket provided to secure against walls
Front access to air filters for ease of cleaning
Front to top air flow for placing agaisnt a wall
Side & rear options for water outlet positions for ease of installation
No Video. See D850 / D950 movie to understand usage
Back plate secures against wall easy to install
Exit points on sides & rear to easily place the dehumidifier
Strong for public spaces such as museums and public changing rooms
Hinged filter compartment at the front allows easy access to filters
Electronic controls & integral humidistat
D850 / D950 CAN BE USED AT POOL SIDE
Ideally hard wired into the mains electricity supply. Keep unit out of direct sunlight. Any shelving above the dehumidifier should be kept to a minimum depth & height above the dehumidifier. Any shelf should not hinder air flow. Avoid any alcoves. Failure to do these points will result in not only poor performance but also will shorten the lifetime of the dehumidifier.
Laws vary by country. In Europe, the minimum distance from a water source for an electrical item is 2 meters.
D850 / D950 / D1100
POSITION IN A TYPICAL TRAINING ROOM
Do not wall mount over the swimming pool. Position at least 2 meters / 6 feet away from the water’s edge. Either drain the condensate back into the pool, to a floor drain or through the wall to the outside.
If the condensate is to the outside ensure there is no prospect of the drain freezing..